|Ticket Number:||20171217_1||Ticket State:||CLOSED|
|Ticket Opened:||2017-12-17 17:24||Ticket Closed:||2017-12-21 14:08|
|Ticket Description:||swiGE2 at UniGE down|
Problem Description:Our router located at UniGE is not reachable anymore.
Access to the console is currently not possible.
Some sites and services connected to swiGE2 have lost redundancy but all traffic is rerouted to backup path.
Affected:From 2017-12-17 17:02 until 2017-12-18 06:42
Impact: no impact
Sites: EPFL-CBT-el2-ge2, HESSO-EIC
From 2017-12-17 17:02 until 2017-12-18 07:12
Impact: no more redundancy
Service: network access
Sites: EHL, skyguide, UNIGE
swiGE2 is up again since 06:42.
The interfaces to UniGE, HUG and Ville-GE flapped until 07:12.
Actually everything seems to be back to normal.
The router stopped because of high temperature.
Our DWDM equipment has high temp as well.
Staff from UniGE is already in the data center.
There is a problem with air conditioning - they try to bring the temp down as fast as possible.
For all questions about this ticket, please send mail to email@example.com
or call +41 44 268 15 30.